Every spring, the wastewater municipality in Dalarna, Sweden, experienced melting snow and heavy rainfall that caused a dramatic increase in pump station inflow. To handle this seasonal volume, the station had oversized pumps that consumed more energy than needed during drier months. This case study illustrates how the installation of a variable-speed pump controller decreased energy consumption by almost 50 percent while allowing for variations in flow.
Ypsilanti’s pumps, originally put into service in 1982, became priority candidates for replacement after operating ten years beyond their expected 20 year service life. The Ypsilanti Community Utilities Authority (YCUA), included the project in the utility’s Master Plan.
As with many plants modified for activated sludge treatment, the existing infrastructure at the Adams Field Wastewater Treatment Plant in Little Rock, AR, allowed rags and other debris to clog the impellers of the submersible pumps. One of the plant’s two 15-horsepower pumps was replaced with an 18-horsepower RAS submersible pump with a self-cleaning impeller, virtually eliminating the clogging problem by simply pumping away any debris that reaches the pump intakes.
Undersized original construction and gradual equipment deterioration led to recurring pump station failures and overflows for the Valley Rural Utilities Company’s wastewater collection system in Lawrenceville, Indiana.
Aging pumps at Jackson Energy Authority’s Rolling Acres Lift Station (Jackson, Tenn.) resulted in frequent clogging and outages that required costly maintenance and repair.
After anticipated growth of the New Jersey casino industry fell short, Atlantic City Sewerage Company’s Baltic Avenue Pump Station was left with grossly-oversized long-shaft sewage pumps that operated inefficiently and were prone to cavitation.
Powerful Pump Monitoring for Optimal Lift Station Performance. Trimble Unity software combined with the Telog wireless, battery-powered, multi-channel recording telemetry system provides a GIS-centric cloud and mobile platform for monitoring lift station pump on/off cycles along with sump levels. Clamp-on current sensors monitor pump run on/off to one second resolution.
Wastewater can be both corrosive and abrasive. To ensure reliable and cost-effective pump operation, it is important to select a wastewater pump made from the most suitable material for your wastewater.
If one debate over a specific design feature stands out amongst all the others in the submersible waste water pump field, it must be, “Which is better, air-filled or oil-filled motors”? With The introduction of premium efficient motors by several manufactures, this topic has come to the forefront once again.
When a motor is operated on a variable frequency drive, unexpected voltage can be induced on the rotor and shaft.
When the discussion turns to requirements for “explosion-proof” pumps, many people rely on word of mouth, past practices or even old wives tales it seems. By Kevin Clemons
Most manufacturers employ a semi-open impellers in their self priming centrifugal sewage and trash pump designs. While other types of impellers, (enclosed, open or recessed), are sometimes used, this type of impeller has a proven field record for clog resistance and high efficiency. By Kevin Clemons